These image galleries contain photos taken while performing our inspections. They show examples of why you should have a ProSpec Home Inspection performed.
Plumbing vent open end in attic space.
Plumbing gases are noxious. Recommend
extending vent pipe up thru roof per code.
Hot water heater has defective flue pipe
connection; a potential hazardous condition.
Water pipe connections corroded due to
dissimilar metal contact. Suggest rigid
tubing and dielectric fittings to prevent
Burner cover missing from 18 yr. old hot
water heater. Suggest plumbing contractor
to service unit and provide burner cover.
Sink drain flexible leader is leaking. Request
seller to repair leak. Suggest replacing flex
leader with rigid PVC connection to the trap.
Toilet waste line leak detected at
lead bend in basement when
tested. Suggest repair.
Water meter with plumbing ground
connection and jumper. Recommend
bronze clamps to avoid dissimilar