- Home Page
- About ProSpec Home Inspection
- Our Pricing
- Sample Reports
- What Our Inspection Includes
- Why Hire Us?
- Our Qualifications
- Photo Galleries
- Client Testimonials
- Pre-Listing Inspections
- Thermal Imaging Reports
- Book an Inspection Online
- FAQs about Home Inspections
- Articles of Interest
- Areas Served / Community Links
- Mobile Site
Plumbing System Photos -- (Click Here)
Plumbing vent open end in attic space.
Plumbing gases are noxious. Recommend
extending vent pipe up thru roof per code.
Hot water heater has defective flue pipe
connection; a potential hazardous condition.
Water pipe connections corroded due to
dissimilar metal contact. Suggest rigid
tubing and dielectric fittings to prevent
Burner cover missing from 18 yr. old hot
water heater. Suggest plumbing contractor
to service unit and provide burner cover.
Sink drain flexible leader is leaking. Request
seller to repair leak. Suggest replacing flex
leader with rigid PVC connection to the trap.
Toilet waste line leak detected at
lead bend in basement when
tested. Suggest repair.
Water meter with plumbing ground
connection and jumper. Recommend
bronze clamps to avoid dissimilar
Write a Review
We'd like to hear from you to assess whether we're doing a good job keeping valued customers like you happy. Please use the links below to grade ProSpec's quality of work and customer service.