- Home Page
- About ProSpec Home Inspection
- Our Pricing
- Sample Reports
- What Our Inspection Includes
- Why Hire Us?
- Our Qualifications
- Photo Galleries
- Client Testimonials
- Pre-Listing Inspections
- Thermal Imaging Reports
- Book an Inspection Online
- FAQs about Home Inspections
- Articles of Interest
- Areas Served / Community Links
- Mobile Site
Electrical System Photos -- (Click Here)
Degraded wire insulation from
overheating due to oversized circuit
breaker. Electrician to correct.
Improperly installed service drip loop
can allow water to enter the service
weatherhead and meter pan.
Electrician to correct.
Corrosion inside electrical panel caused
by water entering via conduit. Suggest
correcting existing water incursion
at defective sill plate.
Sample testing of outlets to check for
proper polarity, grounding, open circuits
and to test GFCI receptacles. Testing
revealed outlets wired in reverse
polarity which is an easy fix.
Electrical panel checked for proper
grounding bond to an acceptable
Improper wiring practice used in attic
space to be corrected.
Write a Review
We'd like to hear from you to assess whether we're doing a good job keeping valued customers like you happy. Please use the links below to grade ProSpec's quality of work and customer service.